Title, Curso de vapor Spirax Sarco. Contributor, Spirax Sarco (Firma). Publisher, Spirax Sarco, Length, 84 pages. Export Citation, BiBTeX EndNote. Curso de Vapor por Spirax Sarco, Tuvanosa, Calzada Aeropuerto # Pte Col. Nuevo Bachigualato, Culiacán, Mexico. Mon Oct 17 at. Curso de gestión impartido en Queretaro, gracias por confiar en Spirax Sarco. Expertos en soluciones de energía térmica y vapor. #atodovapor #spiraxsarco.
|Published (Last):||13 September 2017|
|PDF File Size:||15.56 Mb|
|ePub File Size:||16.79 Mb|
|Price:||Free* [*Free Regsitration Required]|
As soon as steam has left the boiler, some of it must condense, to replace the heat being lost through the pipe wall. Therefore allowance should be made for this pressure loss when deciding upon the initial distribution pressure.
Insulation will naturally reduce the heat loss, but the heat flow and the condensation rate remain as small but finite amounts and if appropriate action is not taken these amounts will accumulate. Sizing one is not difficult as they are always sized to match the steam line line size. The result is that the heat exchange equipment receives very wet steam. The pressure at which the steam is to be distributed is determined by the point of usage on the plant needing the highest pressure.
The result is very wet steam reaching the equipment.
Spirax Sarco Colombia | First for Steam Solutions
It must supply good quality steam at the required rate and at the right pressure. The condensate will form droplets on the inside of the pipe wall, and these can merge into a film as they are swept along by the steam flow. This is one location where a correctly sized mechanical drain trap, such as a float trap, can be beneficial. If this build up continues, the tips of the waves.
Curso de Vapor
Pressure required at point of use Pressure drop along cuurso due to resistance of flow friction Pipe heat losses We also know that steam at a higher pressure occupies less volume per kg. It therefore follows that if we generate steam in the boiler at a much higher pressure than that needed by its application, and we distribute it at this higher pressure the bore of the distribution mains will be saco for any given mass flow rate.
Enviado por Luiz Felipe flag Denunciar. We already know that dry saturated steam not superheated is to be used for process and heating applications and it is that with which we shall concern ourselves.
Steam flowing over this film can raise ripples curdo can build up into waves.
It must do this with the minimum of heat loss, and be economical in capital cost. If taken from the side, or even worse from the bottom, they can carry the condensate from the main and in effect become a drain pocket.
Spirax Sarco Argentina | First for Steam Solutions
Steam leaving a boiler, or other sources, is often much wetter than is appreciated and if this water is not removed, there will be poor heat transfer at the point of use this is why the steam needs d be dry. We must remember however that as the steam passes through the distribution pipework, it will lose some of its pressure due to resistance to flow, and the fact that some of it will condense due to loss of heat from the pipes. If this build up continues, the tips of the waves will break off, throwing droplets of condensate into the steam flow.
The use of a separator to remove this moisture is shown in the slide. This causes considerable damage to the pipework and ancillaries.
Steam lines are no exception. The film will also gravitate towards the bottom of the pipe, and so the thickness of the water film will be greatest there.
Summarising, we need to consider when selecting our working pressure: